16 Jul Wow check out this Meter Base
Wow check out this Meter Base
At first it all looks okay but they were losing power. If you look closely you can see that the Meter Base itself is recessed into the meter base and they have applied Silicone around the meter its self. This was just the first indicator of the problems to come.
After looking inside the base and talking to the owner the power company was called it was just to Dangerous to chance of shorting out to try and do anything even the power company turned the power off before opening it up. Yes it was that bad, after the power was off he removed the meter base and I was able to start checking it out and this is what
Before we even start with the list What they did before was a real danger you can see that at one point it shorted out even with the proper protection the person that did this should have gone to the Hospital to be checked out this was bad really bad. You have to remember that there is really no protection on the side of the power company that is why we install Main breakers.
1st – To start off we found the the socket itself had been Retro fitted from another meter base
2nd – They had relocated the top left lug different from what it was designed to be (These are designed this way to keep clearances so there is no shorting out each and every voltage requires different distances to protect from shorts)
3rd – top left of the breaker the home made buss work obviously has been shorted out even if this was rated for the 200 amp load before it isn’t now when it was shorted they lost material and now it no longer has the design or rating it once had
4th – the lug on the top right of the breaker was modified and has lost its rating as well.
5th – if you look close you can see that the grounding/bonding/neutral Lug is loose and just hanging around to short out when someone moves it just right
6th – The neutral was loose inside the lug
7th – 5 and 6 Were not bonded correctly to the can/housing so if the feeders did short out to the box then it might not trip as needed or required.
Side Note. if you modify the equipment it no longer has the rating it came with and at that point you need the local jurisdiction to approve it.
We highly recommended to the owner to get this meter replaced by a licensed contractor even if we didn’t do it ourselves. They needed to get this Replaced ASAP.
Disclaimer: This is an information blog only. Always contact a licensed and insured Electrical Contractor to work on your home or business.